Create an Account - Increase your productivity, customize your experience, and engage in information you care about.
A licensed contractor will conduct tests on necessary piping for water (head test) and gas (air test, etc); all tests must sustain adequate pressure for 15 minutes.
Show All Answers
The minimum depth required for water service connection is 42 inches. The minimum depth for sewer system drainage is 24 inches.
For areas housing children (such as pre-school, day care and public places), the temperature of hot water should be between 90 degrees and 105 degrees. The temperature of water in private homes should be from 120 to 140 degrees.
The following tasks require backflow preventers: